majority of fires are usually caused in an isolated unoccupied areas
or where no one is around. At that time Extinguishing Fire is impossible,
so in such areas Automatic Modular Fire Protection System is of much
More over plants, equipments and materials are frequently located in
places which are not occupied or visited regularly. Automatic Modular
Fire Protection works for even in a isolated areas and twenty four hours,
round the clock, even at night, weekends and holidays.
The Modular Fire
Protection System is such designed that it is easy to install and works individually
and automatically. Its erection is simple and not costly and unsightly
pipe work is involved.
The Modular body is
manufactured out of two hemi-sphereical M.S.Sheets and are welded
together. They are then Chromium Plated or Powder Coated in Fire
Red Colour as per requirements after Anti Corrosive treatment. Heat
Sensitive Bulbs is fitted in Value Discharge Head of 57°C/68°C
as per requirement to function as Heat Detector and Discharge
Head when suspended from ceiling.
Modular Fire Protection
System units are available with two type of Extinguishing Agents
& BCF Halon 1211 and
are both Pressurised with Nitrogen.
Dry Chemical Powder
Dry Chemical Powder
are most suitable for open spaces and where powder deposition is not
objected by equipments or machineries and where powder can be easily
cleaned such as transformer, storage, workshop, warehouse, etc.
BCF Halon 1211 are
mostly used where equipments or machineries are very sensitive such
as in computer rooms, electrical switch panels, Telephone Exchanges,
etc. where after clean up is not required.
On the temperature
below the discharge head reaching the designed temperature, the glass
bulb bursts and allows the contents of the container to discharge on
the fire risk below, in the form of a 90 degree cone which puts the fire
24 Hours Protection,
Easy Cleanup, Automatic Activation, Self Contained, No Piping, Easy
Installation, Inexpensive, Non toxic, Rechargeable, Suitable for Class
A,B,C and Electric Fires.
Check the total weight
and the pressure indicating gauge regularly. Recharge after use or if
loss in weight or in pressure exceeds 10 %.
2.5 KGS., 5 KGS., 10 KGS., 15 KGS.